The 15000 watt inverter charger is a 48 volt to 120/240Volt split phase pure sine wave power inverter, battery charger and transfer switch.
There is no solar charger built-in, it can’t accept DC power from PV arrays.
This 15000 watt inverter is designed to retrofit the grid tie solar system into an AC coupled off grid system with minimal rewiring required.
The grid tie solar inverter’s AC output power is connected to its AC output.
It with charging algorithm for Lithium Ion Battery LifePo4 EV. It has a set of algorithm customized for the Tesla Model S 48vdc lithium battery module:
Low Battery Cut Off: 36/38Vdc
Low Battery Voltage Alarm/ Charger Activation: 37Vdc
Low Battery Cut Off Recovery: 47Vdc.
Charger Cut Off: 48Vdc
High Battery Alarm/Cut Off: 50.5/51V
If you are looking for a large enough inverter charger for your whole house, this 15000 watt inverter is the right one to opt for.
What is the difference between AC coupling vs DC coupling ?
Traditional off-grid systems are DC-coupled, with the battery bank charged by connecting PV modules to a large solar charge controller, which regulates current and voltage.
With AC coupling, an on grid solar inverter is wired directly to the AC loads panel. The battery bank powers the DC-to-AC inverter, the solar production is fed to the AC loads panel, and the extra power from the AC bus is converted to DC to charge batteries.
Ac-coupling offers more advantage than DC coupling in that it gives the user much more flexibility in system configuration.
Traditional off grid inverter chargers are not designed to regulate the charge from an AC coupled system.
These power inverters normally have no battery over voltage protection when they are in inverter mode. Thus they are unable to prevent battery from overcharge in inverter model when extra power is feed from grid tie inverter to their AC output.
The 15000 watt inverter features Dry Contacts Providing Frequency Switch Between 60Hz / 62.5Hz as the secondary charge control of on grid inverter.
It can control excess energy from the grid tie inverter when the battery bank reaches a voltage within the manufacturer’s limit.
To accomplish this, you can use a voltage-controlled relay to close the dry contact to switch the output freq from 60hz to 62.5Hz, shutting off the grid tie inverter system temporarily.
The HP15048D only outputs 60/62.5hz, NO 50Hz available.
For US customers, pls buy from our customer, EVTV Motor Verks Store.